Challenge: The i-unit group was not satisfied with the audio quality during remote meetings. They were looking for a portable solution with excellent audio quality for use in their conference room but also at their client’s offices.
It is important to note that not all PFC power supplies will cause the UPS overload. However, the incompatibility is most acute
in the one of the following situations:
• A large server class PFC supply (e.g. rated 500W or more) is used with a Back-UPS or Smart-UPS SC.
APC recommends that a true, pure sine wave, server class UPS be used..... ...However if, a [non-pure/simulated/steppe
d sine wave UPS like] Smart-UPS SC or Back-UPS RS is to be used, the UPS should be sized accordingly.
Because of the way active PFC’s operate, they can sometimes overload the UPS with momentary high inrush current. This can occur when the UPS transfers from online to on-battery operation, creating a momentary loss of power (<8ms). The PFC supply may respond by temporarily drawing an excessive amount of current.
Join the community of 500,000 technology professionals and ask your questions.